InfoRelay’s IAD3 data center is located at 12100 Sunrise Valley Dr. Reston, VA 20191, and is one of the two data centers in Reston. The data center is designed to meet the stringent security requirements provided by the federal government and contractors.
The InfoRelay data center provides Reston colocation services to its customers from 1/4, 1/2, and full cabinets, multiple cabinets deployments as well as cage provisioning. The data center is a SAS 70 Type II certified, and provides 285,000 square feet of space, and is raised floor design. The data center security is provided through security guards and video surveillance 24 x 7 x 365 with recording and archiving for 90 days. All the data center access is two factor authentication including biometric hand readers or finger print reader with key card verification. Pre action dry pipe and FM 200 fire suppression with VESDA control is installed for extinguishing any fire breaking out in the data center.
The Reston data center has a reliable power infrastructure. The UPS system in N+1 and 2N configuration with automatic transfer switch between critical components, and Caterpillar diesel generators with 20,000 gallons fuel storage in N+1 configuration protect all the system on the loss of utility power. The data center provides a power density of 180 watts per square feet. The dual power supplies directly to each cabinet. The N+1 configured cooling system automate the temperature of the data center. The facility has temperature zone monitoring system, and also installed with computerized environmental controls with monitoring system.
The InfoRelay data center is a carrier neutral facility and provides connectivity to multiple carriers and service providers. The data center has multiple network paths into the building through diverse conduit and fiber optic connections with local 10 Gigabit failover. 24 x 7 x 365 skilled technical support is provided via customer web portal, priority ticket system, and phone.
Reston, VA 20191
InfoRelay – Reston (IAD3) Data Center Highlights
- SAS 70 Type II Audited
- 1/4, 1/2, and Full Cabinets
- Caged Space
- 285,000 Square Feet of Space
- Raised Floor Design
- Security Guards
- Video Surveillance
- Biometric Hand Reader or Finger Print Reader
- Pre Action Dry Pipe and FM 200 Fire Suppression System
- VESDA Control
- 180 Watts per Square Feet of Power Density
- UPS in N+1 and 2N Configuration
- N+1 Configured Caterpillar Diesel Generators
- 20,000 Gallons Fuel Storage Onsite
- N+1 Configured Cooling
- Temperature Zone Monitoring System
- Computerized Environmental Control with Monitoring System
- Carrier Neutral Facility
- 24 x 7 x 365 Technical Support
- Customer Web Portal Control Facility
- Priority Ticket System and Telephonic Support